 Research
 Open Access
 Published:
Heat transfer analysis of underground Utype heat exchanger of ground source heat pump system
SpringerPlus volume 5, Article number: 1863 (2016)
Abstract
Background
Ground source heat pumps is a building energy conservation technique. The underground buried pipe heat exchanging system of a ground source heat pump (GSHP) is the basis for the normal operation of an entire heat pump system.
Methods
Computationalfluiddynamics (CFD) numerical simulation software, ANSYSFLUENT17.0 have been performed the calculations under the working conditions of a continuous and intermittent operation over 7 days on a GSHP with a singlewell, singleU and doubleU heat exchanger and the impact of singleU and doubleU buried heat pipes on the surrounding rocksoil temperature field and the impact of intermittent operation and continuous operation on the outlet water temperature.
Conclusions
The influence on the rocksoil temperature is approximately 13 % higher for the doubleU heat exchanger than that of the singleU heat exchanger. The extracted energy of the intermittent operation is 36.44 kw·h higher than that of the continuous mode, although the running time is lower than that of continuous mode, over the course of 7 days. The thermal interference loss and quantity of heat exchanged for unit well depths at steadystate condition of 2.5 De, 3 De, 4 De, 4.5 De, 5 De, 5.5 De and 6 De of sidetube spacing are detailed in this work. The simulation results of seven working conditions are compared. It is recommended that the sidetube spacing of doubleU underground pipes shall be greater than or equal to five times of outer diameter (borehole diameter: 180 mm).
Background
As a building energy conservation technique, ground source heat pumps (GSHP) have attracted considerable attention on the basis of rising energy prices and urgent environmental pressure caused by excessive energy consumption. Bhutta et al. (2012) reviewed CFD techniques and concluded that they are good tools to simulate heat exchanger design. The geothermal heat exchangers (GHEs) are the basis for the normal operation of heat pump systems, and the thermal characteristics significantly depend on the rocksoil type and the longitudinal temperature distribution. In addition, heat transfer with the surrounding rocksoil is a complicated and unstable process. There has been significant research into the heat transfer phenomena of GHEs which has been which include experimentation, numerical simulation and theoretical analysis models (Bouhacina et al. 2015; Hu et al. 2013; Nam et al. 2008). Katsura (2008) proposed a method to calculate the rocksoil temperature under a pipegroup heat extraction condition by means of a temperature superposition based on linear heat source theory. Shang (2011) predicted the rocksoil temperature variation between the operation and recovery period of GSHPs by establishing a 3D model of a singlewell, singleU heat exchanger combined with multiaperture theory. The results indicated that the soil properties have a greater influence on the soil temperature recovery than environmental factors did. Choi (2011) applied a CFD numerical simulation method to analyzing the influential factors which contains shank spacing, borehole depth, flow velocity and the differential temperature of the inlet/outlet on the heat transfer rate of the GSHP. The results showed that the borehole depth was found to be the most significant factor affecting the system performance. Additionally, the impact of the saturated soil on the mean heat exchange rate was higher than in unsaturated soil, at 40 %. However, to facilitate the research, it is assumed that the soil is homogeneous.
Generally, the drilling diameter is 100~300 mm (Zhao and Dai 2007). Among all GSHP vertical ground heat exchangers, utubes, annular tubes and single tubes are most commonly used. The Utube is most common due to its simple construction, good heat exchanger performance, high bearing, less tube joints, and unlikely leakage. The Utype side tube spacing is small due to restraints imposed on the well drilling diameter. Due to the existence of temperature differences, heat conduction will occur directly between the two sidetubes, interfering with the ability of the soil to function as an effective heat sink. Thermal interference seriously influences the underground heat exchange of Utype tubes, decreasing the quantity of heat rejection for unit well depth by 20–40 %. More seriously, it will lead to a malfunction of the heat pump refrigerantcycle system, which can stop operation. It was found that increasing the pipe spacing, applying high thermal conductivity backfill soil can enhance the performace of GSHP systems (Dehkordi and Schincariol 2014). Shen (2007) uses a finite unit method to perform quantitative analyses on the hystereses caused by thermal interference. Carli (2010) analyzed the thermal interference in the drill holes by calculating the heat resistance, which makes uses an electrical analogy with lumped capacitances. These thermal resistances were used to solve for the heat transfer in an unsteady state. For the vertical double Utype ground tube, although the quantity of heat exchange for a unit well depth is larger than the single Utype tube, for the same drilling area, thermal interference is more likely to happen because the temperature of several sidetubes is different. The rocksoil’s heat equilibrium temperature not only affects the underground rocksoil heat transfer rate, but is also associated with normal operation and economy of heat pump systems. An ideal temperature range ensures efficient running of the system. In addition, appropriate sidetube spacing not can enhance the heat exchanger efficiency but also can reduce the required drilling diameter. Therefore, this paper establishes a threedimensional heat transfer model for a singlewell, doubleU buried tube based on the rocksoil thermophysical properties. It also accounts for vertical temperature stratification according to underground heat transfer test experiment conditions, and carried out comparison of simulation results for soil temperature and Utube water temperature are compared for single Utype buried pipes and a doubleU buried pipes for continuous operation over 7 days. After that, the paper compares the outlet water temperature changes during the time of continuous operation and intermittent operation for a doubleU heat exchanger. Eventually, the doubleU buried pipe model was established of different sidetube center distance. Thermal interference arising from temperature distribution variation for different sidetubes was also analyzed.
Methods
Governing equation
The process of fluid flow and heat conduction within Utype GHEs follows the law of conservation laws of mass, momentum and energy. The mathematical description of these laws is the controlling equation of the process. Since the Re is 18,116, we use standard kε model to simulate the turbulent flow, which has widely applicability, robustness, and saves computation time. The general governing equation (Tu et al. 2009) is as follows:
Continuity part
Momentum part
Energy part
Turbulent kinetic energy k and turbulent energy dissipationεpart
where u, v, w, stands for the velocity of x, y, z dimension, respectively. ν means kinematic viscosity. t, T, ρ and p stands for time, temperature, density and pressure, respectively; Pr is Prandtl number, which means the ratio of molecular momentum diffusivity and molecular thermal diffusivity. Subscript T stands for turbulent flow, P means the term of turbulent kinetic energy production, and D means the term of turbulent energy dissipation. Constants for the turbulent model are observed as below (Launder and Spalding 1974):
The geometric model
ANSYSICEM CFD (ANSYS I. C. 17.0 2016) preprocessing software to build the geometric model of the singleU and doubleU ground heat exchanger and mesh the model. The simulated Utype tube is a DN25 HDPE tube, with the standard specification, (Sun et al. 2000) which has an outer diameter 25 mm, inner diameter of 20.4 mm, wall thickness of 2.3 mm, and a tube surface roughness of 0.01 mm. According to the Prandtl–Schlichting equation, the thickness of the viscous sublayer is 0.29 mm which indicates that the turbulence is in the hydraulic smooth wall region. The sidetube spacing is 75 mm with drilling a diameter of 130 mm. The ground far boundary semidiameter is 2.5 m, and the distance from the bottom surface to the pipe’s elbow is 1 m. The embedded depth of the tube is 80 m and the tube’s center distance S equal 3 D_{e}. A schematic diagram of geometric model is shown in Fig. 1. Based on the basic model, we build the geometric model of a single well doubleU tube with S/D_{e} = 2.5, 3, 4, 4.5, 5, 5.5, and 6. The cross section is shown in Fig. 2, and the units are mm.
Numerical calculation
ANSYS FLUENT 17.0 (2016) software is used to calculate the current numerical investigation. A finite volume discretization is used in approximating the governing equations. A doubleprecision and pressurebased solver is used in the numerical computation. A nonslip boundary condition is adopted on pipe surface. The SIMPLE algorithm is used for pressure–velocity coupling. A firstorder upwind scheme is adopted to the discretization of all terms. The computation can be considered as converged when the normalized residuals for mass, momentum and energy equations are less than 10^{−6}, 10^{−6}, 10^{−8}, respectively. The final results are the dynamic simulation values with a timestep size of 30 s for 7 days of continuous/intermittent operation. The intermittent operation mode process is within the specific time steps where the inlet velocity and flow mode will go through periodical changes between 0.65 m/s, standard kε mode and 0.0 m/s, laminar mode. The inlet temperature is set as 303 K, during the shutoff operation. The following assumptions can be implemented:

1.
Ignore the influence of surface temperature fluctuations on the ground temperature.

2.
Ignore the influence of the water migration in the soil.

3.
Ignore the thermal contact resistance between Utype tube to backfill material, backfill material to well wall, and well wall to the soil.
Grid generation
The singleU model in this work uses structured meshing while the doubleU models all use a combination of structured and nonstructured meshing. In the simulation, structured meshing and nonstructured meshing can provide the same precision (Shevchuk et al. 2011). To meet the requirement of the turbulence model, we use a growing layer ratio of 1.2 to satisfy the desired y+ value, dividing the prism into six layers where the thickness of first layer is 0.1 mm in the radial direction and is adjacent to the interface of the water domain. Because the entire model is a spindly structure, a mesh size of 100 mm is adopted in the longitudinal direction. The mesh size in the elbow of a Utype tube is small approximately 2 mm, due to centrifugal force. The meshes in the soil part gradually sparse and their minimum size is 20 mm in the radial direction. Various mesh elements (approximately 25 million, 33 million and 40 million in singleU; approximately 30 million, 45 million, and 50 million in doubleU) are generated to pass a mesh independence test. The relative deviations of the average outlet temperature on both Utype tubes between the last two sets of meshes are within 2 %. To reduce the quantity of mesh, the final number of cells for the singleU and doubleU type GHEs systems are 3297878 and 4522149, respectively. Pictures of the mesh are shown in Fig. 3.
Boundary conditions and material’s physical property parameters
The computational domain material physical parameters are shown in Table 1. Boundary conditions are shown in Table 2. The initial temperature of all domains and soil boundary wall temperatures varies according to a quadratic function formula based on a numerical fitting of the experiment. These were compiled by INIT macro and PROFILE macro of UDF programs. Figure 4 shows soil temperature changes.
Results and discussion
Simulation verification
Figure 5 shows the test model of the working condition 2 (S = 3De). When operating continuously for 12 h, the temperature at the outlet of the Utype pipe changes with time. Table 3 is the comparison between the simulation value and the measured value. The definition of heat transfer for a unit well depth of a Utype heat exchanger as follows:
G is the mass flow rate in kg/s. c_{p} is specific heat in J/kg/K; T_{in} is the temperature of water inlet in K. T_{out} is the temperature of water outlet in K. H is the drilling depth in m.
As shown in Fig. 5, the outlet temperature is changing with time in agreement with the experimental data from (Zhang et al. 2009). From Table 3 we can see the simulation value of utube heat transfer at a unit well depth is 102.8 w/m, and the measured value is 108.975 w/m, which is a fractional error of 6.175 %. Thus the simulation results can be observed as valid.
The temperature variation of water along the pipe and rocksoil
In this section, we analyzed the impact of a singleU heat exchanger and doubleU heat exchanger on the surrounding rocksoil temperature and fluid temperature under a continuous operation mode and an intermittent operation mode. Figures 6 and 7 show rocksoil temperature changes under the condition of a singleU and doubleU buried pipe after running for 3 and 6 days at r = 0.078 m along the depth direction and z = −40 m along the radial direction. Figure 6 shows that the singleU heat exchanger raises temperature of rocksoil by 6.91 K and 8.0 K on average at the edge of the borehole and an average change of 38 and 44 % was observed relative to the initial average temperature (291.31 K). Furthermore, the doubleU heat exchanger makes the temperature of the rocksoil rise by 9.39 and 10.38 K on average at the edge of the borehole. The average change rates have reached 51.7 and 57 % compared with initial average temperature. From above we can see that temperature increase rate of the rocksoil gradually decreases as the operation time increases. The impact of the doubleU heat exchanger on the initial temperature of the rocksoil is approximately 13 % higher than that of the singleU heat exchanger. From Fig. 7 it can observed that the temperature of the rocksoil from the far boundary of the drilling location presents an increasing inverse proportional function. The influence of the doubleU buried pipe radius is twice that of the singleU tube. Consequently, it is suggested that the drilling spacing of the singleU buried pipe should be reduced relative to the doubleU buried pipe. Adopting a mixed pipe laying form, the doubleU buried pipes lay on the outermost layer. Figure 8 indicates the serious heat shortcircuiting of the doubleU buried pipe. The decreasing outlet pipe water temperature is obviously higher than that of singleU buried pipe. The mean temperature difference between the inlet and outlet of the singleU buried pipe at the 3rd and 6th day are 4.01 and 3.85 K. Consequently, the rates of heat transfer are 9.423 and 9.047 kw and that of doubleU buried pipe are 3.28 and 3.068 K. The heat transfer rates are 7.71 and 7.21 kw, respectively.
Figure 9a shows the average temperature changes of the outlet fluid for doubleU tube running for 18 h, stopping for 6 h in intermittent operation and finishing with continuous operation for 7 days. The heat transfer rate for the two working condition is determined with Eq. (3) and is plotted in Fig. 9b. Since intermittent operation can realize cyclical recovery of the ground temperature, the water temperature at the outlet remains at the initial stage and is always lower than the continuous operation mode. Although the operation time of the intermittent mode is lower than that of the continuous mode, the extracted energy is 337.33 kw·h, which is higher than the continuous mode (36.44 kw·h) based on Eq. (3). Figure 10 is the temperature changes of the rocksoil at the radial position (r = 0.078 m, r = 1.4 m) and longitudinal direction (Z = −70 m, Z = −30 m). It is found that the temperature variation trend of the rocksoil at the edge of the borehole (r = 0.078 m) is in keeping with the outlet fluid temperature. The temperature will go down rapidly when the GSHP system shutoff, and increases quickly once the system restarts operation. Interestingly, the rocksoil temperature at r = 1.4 m will not decrease with the GSHP system shutoff. The temperature at R = 0.078 m always greater than R = 1.4 m because it continually receives the heat flux from the heat source. This variation trend does not vary with longitudinal depth. The temperature distribution of nearby soil at −40 m during the operation and out of operation time of the first day and the sixth day are shown in Fig. 11. It can be observed on the 1st day of the outage period, the soil temperature along the depth direction around the buried pipes was obviously lower than during the operational period. In the 6th day of intermittent operation, the change became smaller, and the radius of influence on soil the temperature by the buried pipes gradually increased. In addition, because the gradient of temperature rise of the continuous operation mode at the same position is larger than that of the intermittent operation mode as the operation time increases, the ground temperature in continuous operation mode will be unable to recover, resulting in a much lower efficiency than the intermittent operation mode. Under such operation, other auxiliary cooling and heat sources can be adopted to recover the ground temperature at around the buried pipe area to ensure longterm and efficient running of the system.
where G is mass flow rate in kg/s. C _{ p } is specific heat, J/kg/K. T _{ in } is the temperature of water inlet in K. T _{ out } is the temperature of water outlet in K and P is total extracted energy in kW·h.
Analysis on heat transfer characteristics of different sidetube spacing
It can be observed above that the interaction effect of the doubleU heat exchanger branch pipe is more serious than the singleU model. However, the sidetube spacing has a great impact on the heat transfer of the doubleU buried pipe and the selection of proper spacing to achieve economic requirements is worth studying. Under the condition of a sidetube spacing that remains constant, if the tube diameter is bigger, the thermal interference will become more noticeable. Therefore, we use the S/D_{e} value to describe the influence of sidetube spacing to heat transmission effectiveness. Consequently, the branch center distance has reached 2.5, 3, 4, 4.5, 5, 5.5 and 6 De when the heat transfer characteristics of the doubleU buried pipe are at a thermal equilibrium state. It is assumed that there is no thermal interference at an infinitely far location, under the circumstance that the temperature difference between inlet and outlet is 4.6 K. Table 4 shows that the doubleU heat exchanger heat transfer rate (Q) at seven working conditions, and the ratio between the branch center distance and external diameter of pipe (S/De) is represented by the corner marked i. The comparative calculation between heat transfer rate with an infinitely distant branch interval and heat transfer rate at the working conditions is set up as the heat loss caused by tube pitch. Figure 12 shows the heat loss arising from tube spacing changes. From the figure, it can be observed that when the sidetube spacing increases from S/De = 2.5 to 6, the thermal loss factor gradually decreases from 90.66 to 36.17 % with an increasing inlet/outlet temperature differential. When S/De is greater than 5, the downward gradient of thermal loss starts decreasing slightly. Figure 13 is the drilling surface temperature distribution at z = 0. The results show that the hot fluid inside the Utube has a great effect on the temperature distribution of the soil around the tube. With the increasing of the tube spacing, the thermal interference gradually weakens. It’s clear that when S/De is greater than five, the backfill soil temperature around the outlet is lower than the outlet temperature, which indicates that the fluid at the outlet will not directly absorb heat from the inlet.
Figure 14 is the heat exchange variation of a unit well depth under different spacing conditions. It can be observed from the figure that heat exchange amount rises with the increasing sidetube spacing. From −80 to −20 m, the heat flux of unit well depth presents a linearly increasing trend. However, when S/De < 5, the linearly increasing trend tends to fall from −20 to 0 m. However, when S/De ≥ 5, it almost always presents an increasing linear trend. When S/De increases from 4 to 5, the heat transfer amount at a unit well depth increased by 8.76 %. While increasing from 5 to 6, the heat transfer amount at a unit well depth increases by 8.69 %.
Consequently, under a limited buried pipe area, for a doubleU buried pipe system, S/De is suggested to be 5 (with a drilling diameter of 180 mm).
Conclusions
Based on a CFD numerical simulation method, we analyzed the influence of a GHEs system of GSHP’s on the temperature of rocksoil under the working conditions of heat removal and Studies were carried out on three aspects of performance, such as outlet fluid temperature variation of the doubleU buried pipe under continuous operation, intermittent operation and thermal interference arising from different branch pipe spacing. The main conclusion is as follow:

1.
After continuous operation for 6 days, a singlewell, singleU and doubleU GHEs makes the rocksoil temperature increase by 8.0 and 10.38 K at the borehole. In addition, the increasing trend gradually slows down with increasing time. The impact of the doubleU buried pipe on the rocksoil temperature is approximately 13 % higher than that of the singleU buried pipe. The thermal interference generated among sideU tubes of doubleU buried pipe is 25.48 % higher than that of the singleU pipe. In addition, the impact increases over time. The influence radius of the doubleU heat exchanger is twice that of that of singleU heat exchanger.

2.
For intermittent operation mode (running for 18 h and shut down for 6 h), the rocksoil temperature obtained a cyclical recovery, and the extracted energy of intermittent is 36.44 kw·h higher than that of continuous mode, although the running time is less than the continuous mode. It is recommended that other auxiliary cooling and heat sources can be adopted during intermittent operation mode to recover the ground temperature to ensure longterm and efficient operation of the system.

3.
The heat transfer rate of doubleU heat exchanger at the sideU tube at a center distance of S/De as 2.5, 3, 4, 4.5, 5, 5.5 and 6 were compared. It can be observed that when S/De is greater than 5, heat loss decreasing in a small amount. It is undesirable to achieve zero loss from the perspective of economy. In order for this system to be practical, it is suggested to adopt a center distance of S/D_{e} = 5~6 (with drilling diameter of 180~ 205 mm) for singlewell doubleU buried pipe system
Abbreviations
 GSHP:

ground source heat pump
 GHE:

geothermal heat exchanger
References
ANSYS Fluent 17.0 (2016) Ansys fluent theory guide. ANSYS Inc., Pennsylvania
ANSYS I. C. 17.0 (2016) User’s manual. ANSYS, Pennsylvania
Bhutta MMA, Hayat N, Bashir MH, Khan AR, Ahmad KN, Khan S (2012) CFD applications in various heat exchangers design: a review. Appl Therm Eng 32:1–12
Bouhacina B, Saim R, Oztop HF (2015) Numerical investigation of novel tube design for the geothermal borehole heat exchanger. Appl Therm Eng 79:153–162
Carli MD, Tonon M, Zarrella A, Zecchin R (2010) A computational capacity resistance model (CaRM) for vertical groundcoupled heat exchangers. Renew Energ 35:1537–1550
Choi JC, Lee SR, Lee DS (2011) Numerical and analytical analysis of vertical ground heat exchangers: intermittent operation in unsaturated soil conditions. Comput Geotech 38:949–958
Dehkordi SE, Schincariol RA (2014) Effect of thermalhydrogeological and borehole heat exchanger properties on performance and impact of vertical closedloop geothermal heat pump systems. Hydrogeol J 22:189–203
Hu PF, Yu ZY, Na Z, Fei L, Yuan XD (2013) Performance study of a ground heat exchanger based on the multipole theory heat transfer model. Energ Build 65:231–241
Katsura T, Nagano K, Takeda S (2008) Method calculation of the ground temperature for multiple ground heat exchangers. Appl Therm Eng 28:1995–2004
Launder BE, Spalding DB (1974) The numerical computation of turbulent flows. Comput Methods Appl Mech Eng 3:269–289
Nam Y, Ooka R, Hwang S (2008) Development of a numerical model to predict heat exchange rates for groundsource heat pump system. Energ Buildings 40:2133–2140
Shang Y, Li SF, Li HJ (2011) Analysis of geotemperature recovery under intermittent operation of groundsource heat pump. Energ Buildings 43:935–943
Shen GM, Zhang H (2007) Parametric analysis of thermal interference in vertical UTube heat exchangers for GSHP. Acta Energies Solaris Sinica 28(6):604–607 (in Chinese)
Shevchuk IV, Jenkins SC, Weigand B, Wolfersdorf JV et al (2011) Validation and analysis of numerical results for a varying aspect ratio two pass internal cooling channel. ASME J Heat Trans 133(5):1085–1094
Sun M, Xie JL, Feng XS, Li YL, Liu YS (2000) Polyethylene pipes for water supply (GB/T136632000). Standard Press of China, Beijing (in Chinese)
Tu JY, Yeoh GH, Liu CQ (2009) Computational fluid dynamic: a practical approach. Shenyang, Liaoning (in Chinese)
Zhang D, Feng Y, Rong XY (2009) Testing and analysis on underground heat exchange of groundsource heat pump system in a residential district in Chengdu. Build Sci 25(10):49–53 (in Chinese)
Zhao J, Dai CS (2007) Design and application of GSHP system. China Architecture and Building Press, Beijing (in Chinese)
Authors’ contributions
GHP contributed to the analysis and drafted the manuscript. LYZ contributed to meshing generation and data acquisition. All authors read and approved the final manuscript.
Acknowledgements
This study is financially supported by Natural Science Foundation of China (Grant No. 51174170). The authors are grateful to Professor Jianjun Liu for his constructive comments on this paper).
Competing interests
The authors declared that they have no competing interests.
Author information
Rights and permissions
Open Access This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.
About this article
Cite this article
Pei, G., Zhang, L. Heat transfer analysis of underground Utype heat exchanger of ground source heat pump system. SpringerPlus 5, 1863 (2016) doi:10.1186/s4006401635488
Received
Accepted
Published
DOI
Keywords
 Utype ground tube
 Numerical simulation
 Heat transfer rate
 Thermal interference