Optimization of CCGT power plant and performance analysis using MATLAB/Simulink with actual operational data
© Hasan et al.; licensee Springer. 2014
Received: 24 January 2014
Accepted: 13 May 2014
Published: 1 June 2014
In the Modern scenario, the naturally available resources for power generation are being depleted at an alarming rate; firstly due to wastage of power at consumer end, secondly due to inefficiency of various power system components. A Combined Cycle Gas Turbine (CCGT) integrates two cycles- Brayton cycle (Gas Turbine) and Rankine cycle (Steam Turbine) with the objective of increasing overall plant efficiency. This is accomplished by utilising the exhaust of Gas Turbine through a waste-heat recovery boiler to run a Steam Turbine. The efficiency of a gas turbine which ranges from 28% to 33% can hence be raised to about 60% by recovering some of the low grade thermal energy from the exhaust gas for steam turbine process. This paper is a study for the modelling of CCGT and comparing it with actual operational data. The performance model for CCGT plant was developed in MATLAB/Simulink.
With the advent of technological advancement, the dependency of human race on electricity has increased manifolds and keeping in mind the uncontrollable power requirement in almost every minute human activity methods are being taken up to exploit the present natural resources like coal, solar etc. Moreover, necessary up-gradation can be done so as to generate more power than the plant used to do in its normal running time.
A CCGT is one such advancement in the field of power generation. It consists of two units (a) the steam turbine unit and (b) the gas turbine unit. The net power output is the summation of both the independent units.
The two units while being physically independent, depend on each other for their operation. The gas turbine unit is fired first. This results in hot exhaust gases from the turbine. This hot exhaust gas is used to operate the boiler of the steam turbine generating steam. Once steam is generated the operation of the steam turbine starts.
As the above explanation shows, the steam turbine operates from the energy wasted at the exhaust of the gas turbine. Consequently no separate fuel or energy is required to operate the steam turbine. This results in considerable saving of energy while increasing the power generated.
Conversion of hot gases from the exhaust of the gas turbine to heat required for the boiler is done by the Heat Recovery Steam Generator (HRSG) unit.
The input temperature to a steam turbine is about 540°C and the exhaust can be maintained at the atmospheric pressure, due to design consideration the input temperature is limited and the efficiency of the about 40%. The input temperature of the gas turbine can be as high as 1100°C but the exhaust temperature can be lowered to about 500-600°C, the efficiency of a gas turbine is about 33%. It can be seen that to obtain higher efficiencies the exhaust of the gas turbine can used to drive the steam turbine giving efficiency up to 60% (Black & Veatch 1996).
The plant consists of a compressor, combustor, gas turbine, waste heat recovery boiler, steam turbine, and generator(s).
Where Ti is ambient temperature and Pa denotes the atmospheric pressure. W a is air flow with the assumption that P a = Pa 0.
P ro is the design compressor pressure ratio and y is the ratio of specific heats.
Where Wf is fuel flow per unit its rated value, ‘o’ denotes rated value, W denotes the airflow and Td denotes the compressor discharge temperature.
Where η t is turbine efficiency. The exhaust gas flow is practically equal to the airflow.
Where, a = η c η t k1.
Where p p is the isentropic temperature ratio (T2/T1), k1 is the cycle maximum temperature ratio (T3/T1).
The above calculations were done using the following parameters: Pressure Ratio: 8 to 16; Air Fuel Ratio: 50 to 65; Plant Rating: 122 MW for Steam Turbine and 104 MW for Gas turbine.
Description of simulink model
This model consists of various blocks describing various parameters whose variations have to be studied in order to optimize the performance of combined cycle. There are blocks related with speed/load, temperature control, fuel control, air control and other blocks for gas turbine, waste heat recovery boiler/steam turbine, rotor shaft, and temperature transducer.
Speed/Load control block
Temperature control block
Fuel control block
The fuel control block (valve positioner and fuel control) performs according to the minimum value provided by the speed/load control and temperature control and determines the fuel flow Wf. The Min-Max block selects the minimum value between speed/load control and temperature control and the saturation controls the maximum value of the fuel flow. The output of the saturation is modified by various control blocks and then is input to the valve positioner block which controls the positioning of the valve for the fuel flow. The output of the valve positioner is then input a fuel system control block which gives the value of the fuel flow Wf.
Air control block
The air control block (saturation 3 and saturation 4) is to adjust the air flow in the gas turbine to attain a desired exhaust temperature so that the temperature is kept below a reference temperature by an appropriate offset. This arrangement is used to control the compressor inlet guide vanes (IGV). The exhaust temperature of gas turbine Te is compared with a reference temperature which gives the value in ln1. The value of ln1 is compared with offset block and then the output is sent to the air control blocks. The air control blocks adjust the opening of IGV according to the exhaust temperature of the gas turbine. The air flow in gas turbine is used to control the exhaust temperature in the gas turbine.
Results and discussions
Figure 7 shows the plot between overall efficiency and gas turbine efficiency with varying steam turbine efficiency as per the equation (6) (Rai et al. 2013b). It can be seen that combined cycle efficiency increases with the increase of both gas turbine efficiency and the steam turbine efficiency.
The graph in Figure 8 shows the change in gas turbine efficiency for various rate of change in steam turbine with gas turbine efficiency keeping steam turbine efficiency constant = 24%. It shows that if the efficiency of steam turbine is kept constant and the efficiency of gas turbine is varied, the overall efficiency of the combined cycle can be increased but if the value of derivative falls below the R.H.S. the efficiency of combined cycle would drop. The area I shows the region in which there is allowable reduction in steam turbine efficiency with respect to the gas turbine efficiency.
Figure 9 shows the variation of gas turbine efficiency with cycle maximum temperature ratio (T3/T1) keeping the pressure ratio constant in accordance to equation (7). It shows that the turbine efficiency can be increased by increasing the maximum temperature ratio of Brayton cycle. The optimal value of T3/T1 observed as 5.5 This matches with the safe limit of operation of the plant beyond which the plant starts overheating.
The plot (Figure 10) shows how exhaust temperature of the gas turbine varies with the fuel flow as per equation (5). It can be seen that the exhaust temperature increases with the increase in fuel flow. As more energy is supplied temperature increases.
Figure 11 shows the variation of exhaust temperature with time. The exhaust temperature first increases due to more fuel flow till a reference temperature where it is controlled by air flow so that it does not rise any further as it would damage the turbine. From Figure 12 it can be seen that the IGV (Inlet Guide Vanes) start opening to allow more flow of air and thus reducing the exhaust temperature as can be seen by the drop in the exhaust temperature.
Simulation is based on numerical analysis which results in prediction errors while experimental result is the what is actually obtained
Simulation is based on parameters which do not get affected during the simulation process while the parameters provided during experiment can change due to factors beyond the control of the researcher.
Compressor inlet temperature
Compressor discharge temperature
Gas turbine inlet temperature
Gas turbine exhaust temperature
Compressor pressure ratio
Ratio of specific heat
Temperature control integration rate
T c max
Temperature control upper limit
T c min
Temperature control lower limit
F d max
Fuel control upper limit
F d min
Fuel control lower limit
Valve positioner time constant
Fuel system time constant
Air control time constant
Compressor volume time constant
Gas turbine output coefficient
Steam turbine output coefficient
Governor time constant
Gain of radiation shield
Gain of radiation shield
Radiation shield time constant
Thermocouple time constant
Temperature control time constant
Ratio of fuel adjustment
Fuel valve lower limit
Tube metal heat capacitance time constant of waste heat recovery boiler
Boiler storage time constant of waste heat recovery boiler
Turbine rotor time constant
A multi shaft CCGT was considered
CCGT consisted of two gas turbines and one steam turbine
Both gas turbines were of 104 MW
The steam turbine was of 122 MW
HRSG 330 MW
The efficiency of Gas Turbine increases with the maximum cycle temperature ratio. The exhaust temperature of the Gas turbine can be increased up to a limit only due to structural limitations. But inlet Temperature (T1) can be lowered which increases the maximum cycle temperature ratio (T3/T1) which in turn will increase the Gas turbine efficiency (Figure 9).
Improving the gas turbine efficiency alone does not necessarily mean the increase in the overall efficiency of the combined cycle (Figure 7). Increasing the gas turbine efficiency would cause lower input steam temperature for steam turbine for given output temperature so the efficiency of the steam turbine would decrease causing the drop in the overall efficiency of the combined cycle (Figure 8).
The temperature exhaust of the gas turbine is also an important parameter which has to be maintained as by increasing fuel flow more power output can be obtained but it would cause a rise in the temperature but since the temperature has to be limited below a safe value as an increase in temperature can cause the turbine components to get damaged. The temperature is controlled by more air flow in the turbine (Figure 10, Figure 11 and Figure 12).
With the rise in the ambient temperature of the atmosphere the output of the gas turbine falls and the output of the gas turbine can be increased by reducing the inlet temperature of the compressor by cooling of the air that is being fed to the compressor.
When the fuel input to the turbine is increased, for increasing the output, the air flow has also to be adjusted accordingly to prevent the turbine temperature to go above a reference temperature. There is a linear rise in air flow with the fuel flow when the turbine is being operated near its rated value.
Gas Turbine Model – Frame 6, MS9000 series units, 50 Hz application (rotational speed 3000 rpm).
The authors wish to acknowledge the help provided by the staff of Pragati Power Corporation Ltd, New Delhi, India, in providing the necessary experimental data. Special thanks to Prof. Ibraheem, Jamia Millia Islamia, New Delhi, India for extending his guidance during the experiment. The author wishes to thank Rahul Kapoor, Rajesh Garai and Rishabh Kumar Gupta for their contribution in the experiment.
- Al-Zubaidy S, Bhinder FS: Towards optimizing the efficiency of electrical power generation. Energy Conversion Engineering Conference 1996, 3: 1857-1862.Google Scholar
- Black & Veatch: Power plant engineering. Chapman & Hall, New York; 1996.Google Scholar
- de Mello FP, Ahner DJ: Dynamic models for combined cycle plants in power system studies. IEEE Trans Power Syst 1994, 9: 1698-1708.View ArticleGoogle Scholar
- Drbal Lawrence F, Boston Patricia G, Westra Kayla L, Black& Veatch: Power Plant Engineering. Springer; 1996:241.View ArticleGoogle Scholar
- Horlock JH: Advanced Gas Turbine Cycles. Pergamon Press, Pergamon; 2003.Google Scholar
- Kakimoto N, Baba K: Performance of gas turbine-based plants during frequency drops. IEEE Transactions on Power Systems 2003, 18: 1110-1115. 10.1109/TPWRS.2003.814884View ArticleGoogle Scholar
- Kehlhofer R, Bert R, Frank H, Franz S: Combined-Cycle Gas & Steam Turbine Power Plants. PennWell; 2009.Google Scholar
- Kunitomi K, Kurita A, Okamoto H, Tada Y, Ihara S, Pourbeik P, Price WW, Leirbukt AB, Sanchez-Gasca JJ: Modeling frequency dependency of gas turbine output. Proc IEEE/Power Eng Soc Winter Meeting 2001.Google Scholar
- Lalor G, O'Malley M: Frequency control on an island power system with increasing proportions of combined cycle gas turbines. IEEE Power Tech Conference Proceedings, Bologna 2003, 4: 7.Google Scholar
- Rai JN, Naimul H, Arora BB, Rajesh G, Gupta RK, Rahul K: Study the effect of temperature control on the performance of the output of combined cycle gas turbine. International Journal of Theoretical and Applied Mechanics 2013, 8(1):15-23. ISSN 0973–6085Google Scholar
- Rai JN, Naimul H, Arora BB, Rajesh G, Rahul K, Ibraheem : Performance analysis of CCGT power plant using MATLAB/Simulink based simulation. International Journal of Advancements in Research & Technology 2013, 2(5):285-290.Google Scholar
- Rowen WI: Simplified mathematical representations of heavy-duty gas turbines. Trans Amer Soc Mech Eng 1983, 105: 865-869.Google Scholar
This article is published under license to BioMed Central Ltd. This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/2.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly credited.